Precautions in operation and use of gas generating set:
First, before starting the generator every week, the lubricating oil level of the generator and the coolant level of the two water tank shall be checked, and the gas generator shall be prohibited from running at low oil level and low cooling level so as not to damage the generator.
Two, in case of power failure notification, please test the generator operation one day ahead of time to ensure normal operation when power failure occurs! Check the coolant gas pressure, oil level, two water tanks, the generator automatic state transition to the manual state; will universal switch from 3 points to 12 points the direction of rotation to the left direction for the manual state, disconnect the bottom left of the generator circuit breaker; circuit breaker handle to the bottom is disconnected start the generator; will universal switch from 12 points to 6 points to the left direction of rotation direction is the ignition machine.
Three, in case of electric generator can not stop automatically calls after the operation, manual shutdown of generator, direct universal switch from 3 points to 12 points in the direction of the direction, which is above the switch for generator shutdown, power switch, bottom lighting switch, lighting switch in a corner on the left mistress operator, please put on insulation gloves, turn up the triangle wheel, to hear the beep that has switch on power, the cabinet door is closed, the generator by manual to automatic state response production.
We will use good, appropriate service, so that customers feel the warmth of family ties, always depending on the safety of customers, such as ourselves. We will use our natural advantage to create a unique product that will give consumers a unique mood to enjoy the product.