What are the considerations of the gas turbine generator set? Below small make up for you to explain:
1, the gas generator room should be away from the fire area;
2, the gas generator room should be spacious, bright and require the installation of ventilator to ensure good ventilation;
Install 3 gas generator, chassis and application foundation of flat iron pad leveling. The contact area should be in 60% above, and uniform distribution;
4, indoor installation of lighting, switches, circuit and electrical appliances should use explosion-proof measures, and firm fixation;
5, the gas turbine engine room should comply with fire safety requirements, equipped with fire extinguishers and fire fighting equipment;
6, the gas generator room to install the combustible gas alarm, combustible gas leak can be found in a timely manner;
The external main pipe diameter below 60kW 7, a single gas engine gas pipeline shall be not less than 2 inches in diameter, part near the engine should be not less than 1 inches! 60kW gas generator is respectively 3 inch and two inch. And you must install the gas valve (stainless steel ball valve), anti tempering device type drain valve, gas pipeline welding completed, should clean welding slag (with high pressure air);
8, the gas must be desulfurization, dehydration, dust, including flow rate ≤ 0.25Nm3 ≤ 10%, hydrogen.
We have excellent products, perfect service, reliable reputation, for your career success to help, and sincerely welcome colleagues from all walks of life to negotiate business!