The biogas generating unit can be inspected by the owner or the person entrusted by the owner at any time before manufacture, experiment and preparation for transportation. Without planning the company's technical patents and secrets, the owner can understand the production process, plan, experiment and inspection process.
(1) Requirements for Instruments in Experiments
The accuracy of the measuring instruments used in the experiment is as follows:
电流表---0.5% ，电压表-----0.5%， 有功功率表---0.5%，
Amperometer - - 0.5%, voltmeter - - 0.5%, active power meter - - 0.5%.
Reactive power meter - - 0.5%, power factor meter - - 1%, frequency meter - - 0.5%.
The accuracy of the thermometer and pressure gauge used in the experiment is not less than 1 grade.
500V megohm meter is used to measure insulation resistance.
(2) Braking experiment of gas-fired generating units
According to different working conditions, the shutdown test of generator set will be done.
The specific content refers to the contents of the unit experiment in the table below.
(3) Before the unit is matched, the single engine gas engine is tested in accordance with the rules. After the single engine experiment is completed, the generator set is matched with the generator to carry out the factory experiment. All these experiments and testing procedures can withstand the owner's inspection, and complete the experiment report after the experiment is completed.